AGFD – Willow Spring Phs III
- Actuators needed to be installed.
- A Template of the 12″ valve face needed to be taken.
- An inspection of the leaks needed to be quantified.
- The actuators were refurbished.
- Material was gathered for the template.
- Gravel was laid for the new dive.
- Actuators were installed.
- A template was taken.
- Valves are working, but leaking because of bad seals.